With built-in radio-frequency technology and lifetime back-up battery, the FireAngel Pro WHT-230 mains powered heat alarm can be wirelessly interlinked with up to 50 radio-interlinked alarms within a single system. Designed for areas where a standard smoke alarm would be unsuitable, e.g. kitchens and garages, the WHT-230 heat alarm monitors increase in room temperature.
Power: 230V mains powered with back-up battery
Backup: Lithium battery lasts the lifetime of your alarm - GUARANTEED
In a wireless-only system the maximum number of compatible units that can interlink is 50, while a hard-wired-only system is limited to 30 units. In a mixed hard-wired and wireless alarm system these maximum quantities can be exceeded.
For each "group" of hard-wired alarms in a system, only one should be a wireless model. For example, in a 3 storey house you could hard-wire 2x ST-230 and 1x WST-230 alarms together on each floor with all of the WST-230 models wirelessly interlinked to each other. This can technically be done to a maximum of 50 groups of 30 alarms, though FireAngel has not designed, optimised, or tested these alarms for such a large system. Having so many alarms interlinked would create large communication delays between the alarms, potentially resulting in occupants not being given adequate warning of a fire. It is heavily recommended that customers desiring a large amount of alarms for a single property instead look into full Fire Alarm Systems which are designed for larger premises.
The tables below show all the units that can interlink with the FireAngel Pro Wi-Safe 2 alarms.
Q. What smoke alarm should I use in a bedroom with an en suite bathroom?
It is usually recommended to install an optical smoke alarm in a bedroom. This is because optical smoke alarms are slightly quicker at detecting slow smouldering fires that can originate from upholstery type materials and over-heated wiring. Also, an optical smoke alarm would be less likely to sound a false alarm than an ionisation would, if steam/water droplets were present from the bathroom. Detectors should be installed as central to the room as possible; however for your application I would also consider the position of the en suite to make sure that the detector is not in the direct path of the joining door. This is just to try and avoid the chances of a false alarm. No detector is designed for use in bathroom areas.
Q. My ceiling light is on a dimmer switch. Can I still power my radio-interlinked mains smoke alarms from this lighting supply?
In modern housing the lighting circuit will travel around your house with the lights being fed from it. Between the circuit and the light will be a switch (or in this case a dimmer) which will control the light. Your mains powered alarms are connected directly to the circuit and have constant power, so are not affected by switches or dimmers.
In older homes that have not had the electrics updated this may not be the case so it is advisable to consult an electrician.
Q. How do I safely dispose of my old smoke alarms?
Safelincs is signed up to Valpak's WEEE (Waste Electrical and Electronic Equipment) Distributor Take-Back Scheme (Registration ID: 7370). Private households can therefore drop off their electronic and electrical fire safety waste at their municipal recycling centre when they are purchasing new products from us. To find your nearest recycling centre, please visit www.recycle-more.co.uk.
Q. Can the mains powered smoke alarm range be connected to mains power via the lighting circuit?
Yes, hard-wired mains powered alarms can be wired to the unswitched live feed of the nearest frequently used lighting circuit.
Q. If the radio interlinking signal on one unit fails will the units still work as stand alone units.
Yes, should the radio interlinking signal fail the units will continue to sound independently should they detect a fire.