Mains powered with a self-charging lifetime lithium back-up battery, the FireAngel Pro HT-230 heat alarm can be hard-wire interlinked with up to 30 alarms within a single system. The HT-230 heat alarm is quick to detect increase in room temperature, making it ideal for areas where a smoke alarm would be prone to false activation, such as kitchens and garages.
Power: 230V mains powered with back-up battery
Backup: Lithium battery lasts the lifetime of your alarm
In a wireless-only system the maximum number of compatible units that can interlink is 50, while a hard-wired-only system is limited to 30 units. In a mixed hard-wired and wireless alarm system these maximum quantities can be exceeded.
For each "group" of hard-wired alarms in a system, only one should be a wireless model. For example, in a 3 storey house you could hard-wire 2x ST-230 and 1x WST-230 alarms together on each floor with all of the WST-230 models wirelessly interlinked to each other. This can technically be done to a maximum of 50 groups of 30 alarms, though FireAngel has not designed, optimised, or tested these alarms for such a large system. Having so many alarms interlinked would create large communication delays between the alarms, potentially resulting in occupants not being given adequate warning of a fire. It is heavily recommended that customers desiring a large amount of alarms for a single property instead look into full Fire Alarm Systems which are designed for larger premises.
The table below shows all the units that can interlink with the FireAngel Pro alarms.
Q. I want to install an interlinked smoke alarm system throughout my home, but what type of smoke alarms do I need in different rooms?
We recommend a heat alarm in the kitchen, optical alarms in living rooms and hallway and ionisation alarms on landings.
Q. Why do your mains powered alarms have batteries?
All our mains powered alarms have a battery backup. Although mains powered alarms without this option do exist (BS5839 part 6 grade E), we regard them as far too dangerous, as a lot of fires are caused by electrical faults leaving the building unprotected against fire if the smoke alarms have no backup battery. With our mains powered alarms you will always be protected.
Q. What is the best way to test my alarm?
We recommend testing alarms by pressing the test button built-in to the unit, as this is designed to simulate the detection of the target stimuli (usually smoke, heat, or CO) at the alarm sensor. You should test your alarms regularly to ensure they are protecting building occupants, preferably every week. For more detailed guidance, check the manual included with your alarm.
Q. How long do smoke alarms last before needing replacement?
It is recommended that smoke alarms are replaced after 10 years. This is because the sensors in the smoke alarms become less sensitive and may not activate when a fire is present.
Q. Do you need an electrician to connect mains powered smoke alarms?
It is necessary that an electrician installs mains powered smoke alarms.