Fire Safety Information Guide for Landlords
Landlords are responsible for the fire safety of their tenants. Whilst this is a clear enough statement, the considerations and precautions to be taken are challenging. The range of rental properties spanning from single household occupancy to large HMOs or combined residential/commercial properties is wide, especially when taking into account the multitude of occupier profiles (families, disabled or elderly people, drug abusers, etc). And equally varied are the steps landlords must take to find a suitable degree of protection for their particular properties and tenants.
This article describes some of the fire safety considerations for the more common properties and is based on 'normal risk' and able-bodied occupants. Higher risk properties or occupants will require different solutions. The content of this document is intended as a rough guide only and applies only to England, although many parts will apply to Wales as well.
Note: The content of this guide is largely based on the LACoRS guide which may reference older versions of British Standards and legislation. Where possible this guide is kept up to date with the latest revisions of these documents and, as such, may not match the LACoRS guide exactly. This guide is not a substitute for reading the relevant documents and legislation in full or having a Fire Risk Assessment carried out by a competent person.
Which acts and fire safety regulations/guidance apply to your property?
For existing residential premises the Housing Act 2004 applies: this Act includes Housing Health and Safety Rating System (HHSRS), licencing for HMOs, and management regulations for HMOs.
With regards to fire safety, the main legislation is the Regulatory Reform (Fire Safety) Order 2005 (FSO). This Order requires landlords to carry out fire risk assessments in the common areas of HMOs, flats, maisonettes and sheltered accommodation. A guide is available to help landlords carry out fire risk assessments (Sleeping Accommodation Guide).
Note: In premises occupied by single households, only the HHSRS applies.
The responsibilities have been combined and clarified in the LACoRS Guide 'Guidance on fire safety provisions for certain types of existing housing' which applies to owner-occupied, social housing or private rented sector properties such as single household properties, shared houses, bedsit HMOs, purpose-built flats not in compliance with Building Regulations 1991, sheltered accommodation without care, and some small hostels.
The LACoRS guide is not relevant to properties constructed in accordance to Building Regulations 1991 (unless the premises or its purpose are changed), guest houses, bed and breakfast, hotels, motels, large hostels, family accommodation centres, student halls of residence, holiday chalets and others, for which the Fire Risk Assessment guide applies.
More about fire risk assessments
What is a fire risk assessment? An organised and methodical look at the premises, the activities carried on there and the likelihood that a fire could start and cause harm to those in and around the premises. Most premises covered will be relatively small and little fire safety expertise is required to carry out the fire risk assessment. The solutions suggested in the fire risk assessment guide or in the LACoRS guide are not prescriptive and several solutions to fire safety problems are usually possible.
Who is responsible for fire risk assessments and the resolution of any problems identified by the assessment? The person who has control of the premises (landlord or managing agent). That person has to either carry out the fire risk assessment, pass it on to a suitable employee or has to contract out the assessment. Failure to carry out an adequate fire risk assessment or failing to act on its recommendations can result in prison sentences for the fire risk assessor and the responsible person!
- Identify fire hazards
- Identify people at risk
- Evaluate, remove or reduce risk and protect against remaining risk
- Record, plan and inform or train
The fire risk assessment should be documented and updated when the risks or the building are changed.
Identical buildings can have a different outcome from the fire risk assessment, as the type of occupants will determine the risks.
It is recommended that a fire safety log book is kept and all routine maintenance and servicing activity is recorded in it. We offer a free downloadable fire safety logbook and an exclusive free online logbook system.
The following chapters are recommendations largely based on the LACoRS guide. These recommendations cannot be blindly applied to properties but require a fire risk assessment to be carried out as well which will determine higher risk areas or higher risk occupants. The fire risk assessment might even identify a lower than normal risk.
Fire detection is crucial to alert occupiers to the presence of a fire and enables them to evacuate to a place of safety. The fire detection system should be able to wake sleeping people and alert of fires in hidden areas such as boiler rooms. The type of system should be in accordance with BS 5839 Part 6. Grade A and Grade D are the most commonly used grades within the standard.
Grade A: Fire alarm system with detectors and a central control panel. Usually with call-points (break glass units) near exits and on each landing
Grade D: System of (usually interlinked) mains-powered smoke or heat alarms with backup batteries. The interlink can be achieved with cable or radio-interlink. In low risk properties the mains power supply for smoke alarms might be replaced with a requirement for ten year sealed battery supply (usually combined with radio-interlink).
Note: in the 2019 update to BS 5839-6, Grade D was split into D1 (tamper-proof backup battery) and D2 (user-replaceable backup battery).
The coverage within the building by the detection system is described with the following codes:
LD1: Covers all circulation spaces that form part of escape routes plus all rooms in which a fire could start
LD2: Covers all circulation spaces that form part of escape routes plus all rooms and areas that present a high fire risk to occupants
LD3: Covers circulation spaces that form part of the escape routes
There is a degree of flexibility depending on the risk determined in the fire risk assessment, taking into account the types of rooms, dwellings and the occupants' characteristics.
Please note that these recommendations are only applicable for 'normal' risks. Higher risk occupancy or buildings must be identified by a fire risk assessment and will result in a higher standard of protection required.
HMO up to two storeys with no floor greater than 200m2:
Grade D1 Category LD1 throughout.
Other HMOs where each dwelling comprises a single room:
Mixed system: Grade A Category LD2 in common areas, in accordance with BS 5839-1: 2017 Category L2, and with connected heat detectors in bedsits which have cooking facilities. Additionally, Grade D1 Category LD1 in the bedsit itself (not connected to the communal system) to protect the sleeping occupant(s).
Other HMOs where each dwelling comprises a two or more rooms:
Mixed system: Grade A Category LD2 in common areas, in accordance with BS 5839-1: 2017 Category L2. Additionally, Grade D1 Category LD2 in the dwelling itself (not connected to the communal system) to protect the sleeping occupant(s).
Two storey house converted to self-contained flats (prior to 1991 Building Regulations):
Mixed system: Grade D1 Category LD2 in common areas and heat detector in each flat (room / lobby opening onto escape route) connected to the communal system, plus Grade D1 Category LD3 in each flat (not connected to the communal system) to protect the sleeping occupant.
Three to six storey house converted to self-contained flats (prior to 1991 Building Regulations):
Mixed system: Grade A Category LD2 in the common areas, in accordance with BS 5839-1: 2017 Category L2 and with a connected heat detector in each flat (connected to the communal system), plus Grade D1 Category LD3 in each flat (not connected to the communal system) to protect the sleeping occupant.
Single household with fewer than four storeys:
Grade D1 Category LD2 and cellar.
Single household with four or more storeys:
Grade A Category LD1 and cellar.
Flat in multiple occupation (FMO) single storey:
Grade D1 Category LD2 and additional heat detector in the kitchen (and shared living room depending on risk).
The provision of fire blankets and simple fire extinguishers can be useful in restricting the development and spread of small fires in their early stages. However, unless a fire is very small, the best advice is to evacuate the building to a place of safety and call the fire and rescue service.
In HMOs and buildings containing flats, simple multi-purpose extinguishers are required on each floor in the common parts. It will not usually be practical to train tenants in the use of these, but basic advice should be offered at the start of each new tenancy. Whilst powder extinguishers are excellent multi-purpose extinguishers, an inadvertent discharge or deliberate abuse of powder extinguishers can cause substantial damage. Powder extinguishers also reduce visibility and, for this reason, are no longer recommended by the British Standard for indoors use. Landlords therefore need to consider carefully whether foam or even water extinguishers are a suitable alternative. Water mist fire extinguishers, for example, are an excellent alternative, as they can be applied on most fire types, including fat fire and electric fires and cause almost no damage to the interior.
Fire extinguishers should be maintained annually to BS 5306-3. This needs to be done by fire extinguisher service engineers unless service-free extinguishers are deployed. In this case the landlords or their representatives carry out a visual inspection following the guidance of the manufacturer.
Sprinklers are adequate for larger and complex buildings, and where in smaller buildings a landlord is unable to reduce particular risks with other means, sprinklers can be deployed to compensate for these risks.
Compartmentation and fire doors
Compartmentation serves to stop or slow the spread of fire and to allow safe evacuation of a building. Fire escape routes are usually compartmentalised and there can be compartmentation between the different storeys of a building, between cellars/living accommodations and between risk areas and living accommodation etc.
Compartmentation can for example be achieved by specifying minimum standards of plasterboard thickness, as far as walls and ceilings are concerned and by specifying fire resisting doors (fire doors). The two main levels of compartmentation are 30 and 60 minute protection.
There is usually no requirement for formal compartmentation in single household occupancy and low risk shared houses, as long as the construction is sound throughout the route of escape and the doors are close-fitting and sound. Normal glazed doors, flimsy construction and hollow infill-type doors should not be accepted.
Larger properties, however, will require 30 minutes fire protection including fire doors. Their escape routes must be designed to remain free from smoke and fire for a time adequate to allow occupiers of the building to pass safely along it to a place of safety. Usually 30 minute fire doors and sound construction are required unless higher risks are present, in which case 60 minute doors and solid wall separations from risk areas are required. 30 minutes fire resistance in walls can be achieved with solid walls or 12.5mm plasterboard and skim coat. Ceilings must ideally be protected with 12.5mm plasterboard and any ducts must be fire stopped with preferably 60 minutes resistance. See the LACoRS guide for details.
Floor/ceiling partitions between any basement or cellar and the ground floor escape route should usually provide 60 minutes resistance.
Where residential premises are above commercial premises there is usually a requirement for a 60 minute separation between premises and for an interlinked fire detection system in both premises.
Protected escape routes must have no portable heaters or portable heating sources, no cooking facilities, no furniture or storage.
Fire doors help to partition the building into zones. In areas where fire resisting partitions are required, any doorway must be fitted with fire doors. 30 minute partitions require 30 minute fire resisting doors (FD30), 60 minute partitions require 60 minute fire resisting doors (FD60). The letter 'S' after the FD30 or FD60 denotes smoke (cold smoke) seals to be fitted. Most fire doors require intumescent AND smoke seals to be fitted. The exception are fire doors in buildings with smoke detectors only on escape routes (Category LD3), in which case smoke seals should not be fitted so as not to restrict the flow of smoke towards the smoke detectors. It is common to combine intumescent and cold smoke seals into one seal.
Fire doors should mostly be fitted with door closers and must not be wedged open. A fire door which is open cannot stop the spread of fire and smoke, and in most situations it is illegal for a fire door to be without an automatic closer or to be wedged open. For high-traffic routes where occupants are likely to wedge doors, legal solutions are available such as the Dorgard fire door retainer which listens for the sound of an alarm or electromagnetic devices wired in to alarm control panels for Grade A, Grade B, and BS 5839-1 systems.
Fire door signs are only required on fire doors across escape routes and doors to communal kitchens and other communal rooms. They should be marked 'Fire door keep shut'.
Purpose built blocks of flats usually have at least 60 mins fire resistance between the flat and the means of escape, though converted flats may only require 30 minutes of fire resistance or even less. HMOs fall into the second category.
The 2019 revision of the Building Regulations Approved Document B (Fire Safety) Volume 1: Dwellings uses the European classification system (REI) throughout the guidance, with an explanation of this system provided in Appendix B paragraph B19 and a comparison chart between REI and BS 476 ratings in Table B4. In most cases, a BS 476 rating of 60 minutes will usually satisfy REI / EI 60, but confirmation should be sought from the manufacturer, supplier or construction firm to be certain.
Emergency lighting in communal areas
When a fire occurs, people escape in haste and distress. They might be disoriented, especially at night. Staircases and escape routes must therefore be adequately lit, even if the mains power supply is failing as a result of the fire.
Emergency lighting, which will illuminate the escape route after a mains power failure, is therefore required for buildings larger than two storeys. Smaller buildings and single households do not require emergency lighting if the escape route is short and 'borrowed' lighting is shining into the building from the outside.
For dwelling-type buildings that require emergency lighting, it is typically only specified for escape routes rather than throughout the premises as is often the case for commercial buildings. Because of this, it may be referred to as "escape lighting" rather than "emergency lighting", though the function is identical and the terms can be considered interchangeable.
Please note that the requirements for the provision of conventional lighting have been ignored in this article.
Single household occupancy up to six storeys:
Emergency lighting may be required if route is complex and there is no effective borrowed light.
Shared house HMO up to four storeys:
Emergency lighting may be appropriate if route is complex and there is no effective borrowed light.
Shared house HMO five or six storeys:
Emergency escape lighting required
Bedsit HMO up to four storeys (individual cooking):
Emergency escape lighting may be required if building is complex and no effective borrowed lighting available
Bedsit HMO five or six storeys (individual cooking):
Emergency escape lighting required
Houses converted to self-contained flats (up to four storeys) prior to 1991 Building Regulations:
Emergency escape lighting if risk requires
Houses converted to self-contained flats (five or six storeys) prior to 1991 Building Regulations:
Emergency escape lighting required
Flat in multiple occupation (FMO):
Emergency escape lighting if risk requires, may also be required in the common escape route
Emergency escape lighting systems must comply with BS 5266. Emergency lights are required at stairs and changes in floor level or direction and to identify fire alarm points and firefighting equipment. In most cases non-maintained emergency lights providing three hour light will be adequate. The system must incorporate a suitable means for simulating mains failure (i.e. a test switch). Emergency lighting also applies to external escape routes to ensure that occupants can reach a final place of safety outside of the premises. Emergency lighting for stairs should be on a separate circuit to any other part of the escape route.
Fire safety signs
In most residential premises of average size and normal risk, fire safety signs and notices will not be required. However, larger (more than three storeys), complicated premises, and flats are likely to require signage.
To decide if signs are required, consider the following questions:
- Are occupiers familiar with the escape route?
- Is one escape route shorter than others?
- Are there changes in direction?
- Are there any areas where confusion may occur when exiting a building?
- Are there external secondary escape routes which should preferably be used?
- Is there any firefighting equipment that requires signage?
Fire exit signs with directional arrows should provide clear and unambiguous information about the escape route and the fire exit. More guidance can be found in HSE publication 'Safety Signs and Signals: Guidance on Regulations'.
LACoRS guide: Housing – Fire Safety Guidance on fire safety provisions for certain types of existing housing
Download the guide
Fire Risk Assessment guidance
Fire safety risk assessment: sleeping accommodation
Guidance for Fire safety in purpose-built blocks of flats
Download the guide
Approved Document B (Fire Safety) Volume 1: Dwellings
Download the guide
BS 9991 Code of practice for fire precautions in the design, management and use of residential buildings in draft
HHSRS Operating Guidance
Download the guide
HHSRS Enforcement Guidance
Download the guide
Gas Safety (Installation and Use) Regulations 1998
Download the guide
Safety signs and signals. The Health and Safety Regulations 1996. Guidance on Regulations
Download or buy online
Electrical Equipment (Safety) Regulations 2016
Download the guide
Furniture and Furnishings (Fire) (Safety) Regulations 1988
Read the full legislation
Download the Furniture Industry Research Association’s guide to the UK regulations
The small print
The above compilation was done to our best knowledge and only reflects a small part of the relevant fire safety guidance. Certain aspects of fire safety in HMOs e.g. surface finishes and floor coverings in escape routes, fire escape windows, fire exit designs, furniture fire resistance, maintenance regimes and general fire prevention have not been addressed. This text cannot be a replacement for reading the original texts. It can also be out of date. This editorial is intended to give the reader a rough overview over this complex area of legislation and recommendations. For a more detailed assessment of individual buildings, the reader is advised to ask a fire risk assessor to visit the premises in question and provide a written assessment.
Reviewed: 16/01/2020 (doc:122 V1.2). Our articles are reviewed regularly. However, any changes made to standards or legislation following the review date will not have been considered. Please note that we provide abridged, easy-to-understand guidance. To make detailed decisions about your fire safety provisions, you might require further advice or need to consult the full standards and legislation.