The FireAngel Pro ST-230 optical smoke alarm is mains powered with a 10 year sealed lithium back-up battery. Designed to last the life of the alarm, the back-up battery continues to provide power in the event of a mains failure. The ST-230 smoke alarm can be interlinked (using cable) with up to 30 smoke and heat alarms from the FireAngel Pro series, providing wide coverage within a single smoke alarm system. Once interlinked, if the ST-230 smoke alarm is activated, it triggers all other linked alarms to also sound.
- 230V mains powered smoke alarm
- Sealed 10 year back-up battery - no need to replace for the life of the alarm
- CE marked and Kitemarked to BS EN 14604
- Safelincs Exclusive 5 Year Warranty
- Up to 30 FireAngel Pro alarms can be hard-wire interlinked within a single system
- Suitable for installations complying to BS 5839-6: 2013 Grade D, E and F
- Thermally enhanced optical smoke sensor (Thermoptek technology)
- Less prone to false alarms caused by cooking fumes
- Test, hush and "Sleep-Easy" function
- Locate function: allows you to find the alarm that activated the system
- Tamper-proof mounting plate locks the alarm head in place
- Suitable for bedrooms, living rooms and downstairs hallways (not suitable for kitchens or garages)
- Supplied with fixings; 2 x screws and 2 x rawl plugs
This is the technical data for the Mains Powered Thermally Enhanced Optical Smoke Alarm with Lithium Back-up Battery - FireAngel Pro ST-230.
|Alternative Product Codes
||10 year sealed lithium
||-10 °C to +45 °C
Q. What smoke alarm should I use in a bedroom with an en suite bathroom?
A. It is usually recommended to install an optical smoke alarm in a bedroom. This is because optical smoke alarms are slightly quicker at detecting slow smouldering fires than can original from upholstery type materials and over-heated wiring. Also, an optical smoke alarm would be less likely to sound a false alarm than what an ionisation would do if steam/water droplets were present from the bathroom. Detectors should be installed as central to the room as possible; however for your application I would also consider the position of the en suite to make sure that the detector is not in the direct path of the joining door. This is just to try and avoid the chances of a false alarm. No detector is designed for use in bathroom areas.
Q. How do I safely dispose of my old smoke alarms?
A. Safelincs is signed up to Valpak's WEEE (Waste Electrical and Electronic Equipment) Distributor Take-Back Scheme (Registration ID: 7370). Private households can therefore drop off their electronic and electrical fire safety waste at their municipal recycling centre when they are purchasing new products from us. To find your nearest recycling centre, please visit www.recycle-more.co.uk.
Q. Can the mains powered smoke alarm range be connected to mains power via the lighting circuit?
A. Yes, hard-wired mains powered alarms can be wired to the unswitched live feed of the nearest frequently used lighting circuit.
Q. How long do the batteries last in smoke alarms?
A. The 9V alkaline batteries last 12~18 months. Lithium batteries will usually last 5x longer than their alkaline counterparts, achieving around 5 years lifetime. Some lithium cells are also rechargeable, and when used in a mains-powered alarm may last for the entire functional lifespan of the alarm. Newer alarm models may also feature a "sealed" lithium battery. These batteries are specialist components which are designed to not be removed or need replacing by the user, and have been tested by the alarm manufacturer to ensure they last for the lifetime of the alarm.
Please Note: the actual lifetime of your batteries depends on how often the alarms are tested or activated, as sounding the alarm draws more power than when the alarms are "waiting" to detect fire. You should also read your alarm's manual to make sure you only use the recommended types and brands of batteries, as failing to follow these instructions may cause the alarm to malfunction, not alerting you in the event of a fire, and might also invalidate the warranty.
Q. If a false alarm goes off can pressing the hush button on any of the interlinking alarms stop all the units beeping?
A. No, to stop the alarms from sounding the hush button on the unit that started the process needs to be pushed. Pressing any other unit will just silence that one unit. The unit can be identified by the rapidly flashing red LED.
Show all FAQs
Key Product Features
Easy-to-use test/hush button takes centre stage
Break-out tab for seamless trunk wiring connection
3 coloured LEDs show you its status at a glance
Screws and rawl plugs for installation are included
- 1 x FireAngel Pro ST-230 optical alarm
- 1 x Sealed 10-year lithium battery
- 1 x Screw fixing set (screws & rawl plugs)
- 1 x Instruction manual
4 customers have rated this product and it has an overall rating of 5 out of 5
All our reviews are written by real customers that have purchased this product from us and are publsihed without modification.
Reviewed by: ID
Easy to install and a good price, does the job.
There are prettier ones but these meet all specs
Published on: 26th February 2017
Reviewed by: SD
replaced different manufacuter (Firex) with this one easily
Published on: 22nd February 2017
Reviewed by: TB
Nice bug hush button. Discrete design
Published on: 17th January 2017
Reviewed by: -
Published on: 17th December 2015