The FireAngel W1-R series of alarms are available as either a heat or optical smoke alarm, both of which are mains powered with a replaceable 9V back-up battery. Both alarms feature a large, central silence button which also acts as a test button the SW1-R optical smoke alarm while the HW1-R heat alarm has a separate button for testing. Up to 12 W1-R and W1-PF series alarms can be interlinked together via a dedicated cable, including the CW1-PF-T mains powered carbon monoxide alarm, to provide full coverage and reliable warning of possible danger throughout the premises. These alarms also feature a 'safety clip' which prevents them from being installed without a battery, to ensure there is a back-up in case of a mains power failure.
- Power: 230V mains powered with battery back-up
- Backup Battery: 9V alkaline battery (included)
- Warranty: 5 year warranty
- Available in Optical Smoke and Heat detector versions:
- SW1-R Optical Smoke Alarm: ideal for hallways, landings, bedrooms, living rooms, and home offices
- HW1-R Heat Alarm: ideal for kitchens, attics, and garages
- Up to 12 alarms can be hard-wire interlinked within a single system
- Easily perform weekly tests at the push of a button
- Uses the latest detection technologies to reduce nuisance alarms
- Can also be interlinked with the CW1-PF-T mains powered carbon monoxide alarm
- Integrated 'safety clip' feature prevents them from being fitted without a battery
- Large silence button central to the alarm
- Suitable for Grade D2 installations
- Kitemarked to and
- Alarms sold separately
The table below shows all the units that can interlink with the FireAngel W1-R alarms.
||Type of unit
||Type of interlink
||Mains Powered Optical Smoke Alarm
||Mains Powered Heat Alarm
||Mains Powered Carbon Monoxide Alarm
This is the technical data for the FireAngel Mains Powered Alarms with 9V Alkaline Back-up Battery W1-R Series.
|SW1-R Optical Smoke Alarm
|HW1-R Heat Alarm
||SW1-R Optical: 42x126mm
HW1-R Heat: 49x126mm
||9V PP3 Alkaline or Zinc Carbon
||85dB at 3 metres
||+5 °C to +38 °C
The following datasheets are available for this product.
Q. How do I safely dispose of my old smoke alarms?
Safelincs is signed up to Valpak's WEEE (Waste Electrical and Electronic Equipment) Distributor Take-Back Scheme (Registration ID: 7370). Private households can therefore drop off their electronic and electrical fire safety waste at their municipal recycling centre when they are purchasing new products from us. To find your nearest recycling centre, please visit www.recycle-more.co.uk.
Q. Can the mains powered smoke alarm range be connected to mains power via the lighting circuit?
Yes, hard-wired mains powered alarms can be wired to the unswitched live feed of the nearest frequently used lighting circuit.
Q. is there a different alarm sound for optical and heat sensors to tell you the difference in what kind of fire it is?
There is only one alarm sound type when a fire is detected, when interconnected all smoke and heat alarms will sound. However only the triggered alarm will have a rapidly flashing red indicator.
Q. How long do the batteries last in smoke alarms?
The 9V alkaline batteries last 12-18 months. Lithium batteries will usually last 5x longer than their alkaline counterparts, achieving around 5 years lifetime. Some lithium cells are also rechargeable, and when used in a mains-powered alarm may last for the entire functional lifespan of the alarm. Newer alarm models may also feature a "sealed" lithium battery. These batteries are specialist components which are designed to not be removed or need replacing by the user, and have been tested by the alarm manufacturer to ensure they last for the lifetime of the alarm.
Please Note: the actual lifetime of your batteries depends on how often the alarms are tested or activated, as sounding the alarm draws more power than when the alarms are "waiting" to detect fire. You should also read your alarm's manual to make sure you only use the recommended types and brands of batteries, as failing to follow these instructions may cause the alarm to malfunction, not alerting you in the event of a fire, and might also invalidate the warranty.
Q. Do you need an electrician to connect mains powered smoke alarms?
It is necessary that an electrician installs mains powered smoke alarms.
Q. What is the difference between an ionisation and an optical (photoelectrical) smoke alarm?
Ionisation smoke alarms detect fast flaming fires and are suitable for landings. Optical smoke alarms detect slow smouldering fires typical for burning soft furnishings. Optical alarms are suitable for living rooms and sleeping areas and are used near kitchens as they are less prone to false alarms. Please note that ionisation alarms contain a small amount of radioactivity.
Q. How long do smoke alarms last before needing replacement?
It is recommended that smoke alarms are replaced after 10 years. This is because the sensors in the smoke alarms become less sensitive and may not activate when a fire is present.
Q. Can I put my smoke alarm on the wall, or must it be mounted on the ceiling?
The best location to install your smoke alarm is in the centre of the ceiling rather than on the wall. During a fire, smoke initially rises and then spreads to the sides of the room. By installing the alarm on the ceiling, this ensures that you receive the earliest possible warning of a fire.
Q. Why do your mains powered alarms have batteries?
All our mains powered alarms have a battery backup. Although mains powered alarms without this option do exist (BS5839 part 6 grade E), we regard them as far too dangerous, as a lot of fires are caused by electrical faults leaving the building unprotected against fire if the smoke alarms have no backup battery. With our mains powered alarms you will always be protected.
Q. I want to install an interlinked smoke alarm system throughout my home, but what type of smoke alarms do I need in different rooms?
We recommend a heat alarm in the kitchen, optical alarms in living rooms and hallway and ionisation alarms on landings.