The Ei603 heat alarm detects fire by sensing the rise in temperature of its surroundings rather than sampling the air, and its sealed 10 year lithium battery means the alarm will continue to provide continuous detection without the need to regularly replace its batteries. By detecting heat instead of smoke the Ei603 will not suffer nuisance alarms caused by large amounts of dust, cooking fumes, and steam as traditional smoke alarms would, making this alarm suitable for the loft, kitchen, or garage.
This is the technical data for the 10 Year Sealed Lithium Battery Heat Alarm - Ei603.
|Alternative Product Codes||EI603, Ei603, Ei603C, Ei603C-D, Ei603TYC, Ei603TYC-D|
|Sensor Type||Thermistor - activates at 58°C|
|Battery Type||Sealed 10 Year Lithium|
|Sound Output||85dBA at 3 meters|
|Temperature Range||Operating: 0°C to +40°C
Storage: 0°C to +35°C
|Humidity Range||15% to 95% Relative Humidity|
The following datasheets are available for this product.
Q. What smoke alarm should I use in a bedroom with an en suite bathroom?
A. It is usually recommended to install an optical smoke alarm in a bedroom. This is because optical smoke alarms are slightly quicker at detecting slow smouldering fires than can original from upholstery type materials and over-heated wiring. Also, an optical smoke alarm would be less likely to sound a false alarm than what an ionisation would do if steam/water droplets were present from the bathroom. Detectors should be installed as central to the room as possible; however for your application I would also consider the position of the en suite to make sure that the detector is not in the direct path of the joining door. This is just to try and avoid the chances of a false alarm. No detector is designed for use in bathroom areas.
Q. How do I safely dispose of my old smoke alarms?
A. Safelincs is signed up to Valpak's WEEE (Waste Electrical and Electronic Equipment) Distributor Take-Back Scheme (Registration ID: 7370). Private households can therefore drop off their electronic and electrical fire safety waste at their municipal recycling centre when they are purchasing new products from us. To find your nearest recycling centre, please visit www.recycle-more.co.uk.
Q. Can a smoke alarm be fitted with a sticky adhesive pad in a let property?
A. The sticky pad is suitable for all battery operated smoke alarms. However, we cannot judge if battery alarms are suitable for your let property, as let properties usually require mains powered alarms. There is some advice to this in the governments guides to fire risk assessments. http://www.safelincs.co.uk/Fire-Risk-Assessment/
Also see the LACoRS guide for let properties.
Q. How are smoke alarms fitted to the ceiling?
A. Smoke alarms can be either screwed to the ceiling using the holes on the base plate (screws provided) or fixed using a sticky pad, this can be added to your basket through the ordering process.
Q. Do the Ei600 series alarms need 230v or do they just use battery?
A. The Ei600 series of radio-interlinked alarms are completely battery operated. This means that they do not need to be wired up to the mains circuit. On the website, we offer the Ei600 series with a standard 9v battery or with a 10 year lithium longlife battery. The standard 9V batteries last approximately 12-18 months depending on how often the detectors are tested. The lithium battery units are sealed and last 10 years i.e. the full lifespan of the detector.Show all FAQs
|Product Code: EI603||
10 in stock Expected dispatch: Today
£47.27 inc VAT
£39.39 ex VAT
The following delivery options are available on this product.