Your Basket has 0 items
Goods Total: £0.00 ex VAT
When choosing smoke alarms it can be hard to find the right type of alarm for a particular room in your house, tenanted property or workplace. Manufacturers have over the years developed a range of different smoke alarm sensors - and for very good reasons! Fitting the right type of alarm in the right room will not only reduce false alarms but also identify real fire hazards quicker. Below you will find a list of rooms together with the type of alarm you should fit and a brief explanation as to why.
Ionisation smoke alarms have traditionally been used throughout properties for many years. Designed to react quickly to fast flaming fires, ionisation smoke alarms are most sensitive to small particles. When fires produce little or no smoke but the fuel is subject to rapid combustion, the ionisation smoke alarm is the quickest to sense its presence. These fires tend to originate from materials such as paper and clothing.
If you are unsure what type of smoke alarm you have installed, see if you can find a radioactive symbol or compartment inside the alarm (if this is accessible). Unlike optical smoke alarms, ionisation smoke alarms feature a tiny radioactive source in the sensor chamber that enables the ionising technology to work. It's quick reaction to small particles can make the ionisation smoke alarm prone to false alarms, particularly when located near kitchens. Because of this, it is recommended for ionisation alarms to be installed in stairwells, upstairs landings and offices. This should avoid the occurrence of nuisance alarms when cooking or burning toast!
Less prone to false alarms than ionisation, optical smoke alarms are slightly quicker at detecting slow smouldering fires that tend to produce a lot of smoke. These fires tend to originate from upholstery type materials or over heated wiring. Also known as photo-electric alarms, this quick response time to smouldering fires is down to the optical smoke alarm's high sensitivity to large particles in the air. The optical sensing chamber effectively "sees" when smoke is present, as the large particles block and cause an infrared light to scatter.
Optical smoke alarms are suitable for installing in bedrooms and living rooms where soft furnishings and cables are common place. As well as this, optical alarms can be installed in downstairs hallways as it is significantly less likely than ionisation to sound falsely when cooking fumes are present from the kitchen. Optical alarms are not suitable for areas open to the elements and very dusty environments.
Responsive to heat rather than smoke, heat alarms are ideal for installing in kitchens where they are designed to detect a rapid change in temperature. Featuring a fixed temperature thermistor, heat alarms are triggered when the temperature inside the room reaches approximately 58 °C. This specific heat sensing technology avoids false alarms altogether, as the unit does not react to cooking fumes and steam. Please always refer to the manufacturer's instructions for the optimum ceiling positioning - typically about 1m from the cooker. Heat alarms are also suitable for installing in garages. If vehicle fumes are present, a smoke alarm may become a nuisance with sounding falsely.
Conforming to BS 5839 Pt 6 grade D, mains powered smoke and heat alarms contain a back-up battery. In the event of a mains failure, the back-up battery ensures that the alarm will continue to power until the mains feed is restored. Safelincs offers a range of mains powered alarms, where customers can choose from standard alkaline, non-rechargeable lithium upgrade or sealed in lithium back-up battery. Mains smoke and heat alarms with an alkaline battery back-up provide the cheapest (up front cost) solution. Depending on how often the alarms are tested, the back up battery will last approximately 12-18 months before replacement is required. Manufacturers recommend for the battery to be replaced every 12 months to ensure a low running battery is not forgotten. Mains powered smoke alarms have the option to upgrade to non-rechargeable lithium back-up battery. Although not sealed in the alarm, the battery will last 10 years before replacement; with the exception of when used with radio interlinked alarms (2-5 years lifespan). Finally, mains powered alarms are available with a sealed in rechargeable lithium back-up battery. This battery is designed to last the life of the alarm (10 years) and can not be tampered with during its lifespan. As well as saving costs from replacement, the sealed lithium battery option is ideal for rented properties where the removal of batteries or leaving them to run flat could be an issue.
To obtain a mains feed, smoke and heat alarms can be wired to the nearest lighting circuit or through a dedicated circuit from the distribution board. Power supply from the light fitting is generally preferred as it is more cost-effective and less likely to be disabled to stop the "nuisance" of beeping alarms should the back-up battery run low.
Whilst mains smoke alarms give you peace of mind for many years without false alarms or defects, it is dangerous to assume that they work forever. Smoke and heat alarms should be replaced after ten years, as they then start to become unreliable.
You will typically find the following smoke alarm requirements:
Mains-powered, interlinked smoke and heat alarms. These are usually powered with a cable from the nearest light fitting. To create an interlink (all alarms go off at the same time in the case of a fire) they either require cable connection between the units or a radio-interlink connection. In businesses and larger let properties, these are often combined with manual break points.
With the appearance of ten year sealed smoke alarm units with radio-interlink, these are becoming more acceptable as an alternative to mains-powered, interlinked smoke alarms. Radio-interlinked manual break points are also available. However, we still recommend you check with your Building Inspector (in case of extensions), Local Council (rented accommodation) to ensure these alternative alarms are acceptable.
Battery powered, free standing smoke and heat alarms. On their own, they are mainly designed for domestic, owner-occupied housing. However, F Grade alarms with radio-interlink (especially when provided with 10 year sealed lithium batteries) can sometimes be applied as if they were Grade D. Again we recommend that you check first with the relevant authority.