The FireAngel LSI-601 is an ionisation smoke alarm with a built-in Bluescape ultra bright LED light, designed to help illuminate the escape route in the event of an emergency. Upon detection of fire, the LSI-601 smoke alarm sounds an 85dB warning alarm and the LED light automatically illuminates to provide visibility. The FireAngel LSI-601 is independently tested to the latest standards and has 5 years manufacturer's warranty.
Battery powered smoke alarm - 9V alkaline battery included
CE marked and tested to BS EN 14604
Test and hush button feature
Built-in Bluescape ultra bright blue LED light
Helps to illuminate your escape route in an emergency
Ionisation smoke sensor - quick to detect fast-flaming fires
Q. Do I need an ionisation or optical smoke alarm?
We recommend using an optical smoke alarm in hallways, as these are less likely to go off because of cooking fumes from a connected kitchen. Optical smoke alarms are also ideal for living rooms, dining rooms, bedrooms, as they are good at detecting smouldering fires from soft furnishings. For landings we recommend ionisation alarms. Heat alarms are designed for kitchens and garages. No alarms should be installed in bathrooms.
Q. Can I put my smoke alarm on the wall, or must it be mounted on the ceiling?
The best location to install your smoke alarm is in the centre of the ceiling rather than on the wall. During a fire, smoke initially rises and then spreads to the sides of the room. By installing the alarm on the ceiling, this ensures that you receive the earliest possible warning of a fire.
Q. What is the best way to test my alarm?
We recommend testing alarms by pressing the test button built-in to the unit, as this is designed to simulate the detection of the target stimuli (usually smoke, heat, or CO) at the alarm sensor. You should test your alarms regularly to ensure they are protecting building occupants, preferably every week. For more detailed guidance, check the manual included with your alarm.
Q. How long do smoke alarms last before needing replacement?
It is recommended that smoke alarms are replaced after 10 years. This is because the sensors in the smoke alarms become less sensitive and may not activate when a fire is present.
Q. What sort of smoke alarm system would I need to install for a HMO?
BS 5839-6 recommends that one or two storey HMOs with an individual floor area of no more than 200sqm (not the total of both floors) should have a Grade D smoke alarm system installed. Grade D refers to mains powered smoke alarms with a back up battery power supply. The alarms can be interlinked either by wire or by radio signal and the system does not require a separate fire alarm panel. For HMOs of 3 storey or higher, a Grade A panel system would need to be installed. This can cover the whole of the building, or can be used just for the communal areas with a separate Grade D system installed for the individual dwellings. For both applications, the level of cover should be a minimum of LD3 (in all escape routes) but this may change according to the fire risk assessment.