UltraFire battery powered heat and optical smoke alarms can be radio-interlinked with each other, up to a total of 50 units, to create a wireless alarm system within your home. Powered by two 1.5V alkaline AA batteries, these alarms have a wireless range of up to 100m in open air and 35m indoors. Heat alarms are designed for use in areas prone to false alarms caused by dust or steam and cooking fumes, such as kitchens, garages and unconverted loft spaces. Optical smoke alarms are less susceptible to false alarms caused by cooking fumes, making them suitable for installation near (but not in) kitchens as well as in living rooms, bedrooms, hallways, and landings. Optical smoke alarms are also suitable for rooms which have traditionally been protected by ionisation alarms.
- Battery powered alarms - AA batteries included
- If one alarms detects smoke / fire, all alarms in the system will sound
- CE marked, certified and Kitemarked
- Smoke Alarm: certified to BS EN 14604:2005
- Heat Alarm: Kitemarked to BS 5446-2
- Suitable for installations complying to Grade F
- Both alarms feature a large central test / hush button
- A total of 50 compatible units can be interlinked
- Digital 'house coding' prevents interference from neighbouring systems
- RF range of 35m in buildings (100m outdoors)
- No central alarm panel or master unit required
- Supplied with fixings: 2 x screws and 2 x rawl plugs
This is the technical data for the Radio-Interlinked Battery Powered Smoke & Heat Alarms - UltraFire UB1RF Series.
||UBS1RF Smoke Alarm: 35x125mm
UBH1RF Heat Alarm: 40x102mm
||2 x AA alkaline
||85dB at 3 metres
||0°C to +40°C
|Relative Humidity (non-condensing)
||UBS1RF Smoke Alarm: Up to 93%
UBH1RF Heat Alarm: 10% to 95%
The following datasheets are available for this product.
Q. How do I safely dispose of my old smoke alarms?
A. Safelincs is signed up to Valpak's WEEE (Waste Electrical and Electronic Equipment) Distributor Take-Back Scheme (Registration ID: 7370). Private households can therefore drop off their electronic and electrical fire safety waste at their municipal recycling centre when they are purchasing new products from us. To find your nearest recycling centre, please visit www.recycle-more.co.uk.
Q. How long do the batteries last in smoke alarms?
A. The 9V alkaline batteries last 12~18 months. Lithium batteries will usually last 5x longer than their alkaline counterparts, achieving around 5 years lifetime. Some lithium cells are also rechargeable, and when used in a mains-powered alarm may last for the entire functional lifespan of the alarm. Newer alarm models may also feature a "sealed" lithium battery. These batteries are specialist components which are designed to not be removed or need replacing by the user, and have been tested by the alarm manufacturer to ensure they last for the lifetime of the alarm.
Please Note: the actual lifetime of your batteries depends on how often the alarms are tested or activated, as sounding the alarm draws more power than when the alarms are "waiting" to detect fire. You should also read your alarm's manual to make sure you only use the recommended types and brands of batteries, as failing to follow these instructions may cause the alarm to malfunction, not alerting you in the event of a fire, and might also invalidate the warranty.
Q. How are smoke alarms fitted to the ceiling?
A. Smoke alarms can be either screwed to the ceiling using the holes on the base plate (screws provided) or fixed using a sticky pad, this can be added to your basket through the ordering process.
Q. What sort of smoke alarm system would I need to install for a HMO?
A. BS 5839-6 recommends that one or two storey HMOs with an individual floor area of no more than 200sqm (not the total of both floors) should have a Grade D smoke alarm system installed. Grade D refers to mains powered smoke alarms with a back up battery power supply. The alarms can be interlinked either by wire or by radio signal and the system does not require a separate fire alarm panel. For HMOs of 3 storey or higher, a Grade A panel system would need to be installed. This can cover the whole of the building, or can be used just for the communal areas with a separate Grade D system installed for the individual dwellings. For both applications, the level of cover should be a minimum of LD3 (in all escape routes) but this may change according to the fire risk assessment.
Q. How long do smoke alarms last before needing replacement?
A. It is recommended that smoke alarms are replaced after 10 years. This is because the sensors in the smoke alarms become less sensitive and may not activate when a fire is present.
Show all FAQs