This product has been discontinued.
£6.42 inc VAT
£5.35 ex VAT
The FireAngel ST-625 smoke alarm uses Thermoptek optical smoke sensing technology; making it thermally enhanced and quicker to detect smouldering fires compared to standard optical smoke alarms. Featuring a large test/hush button, the FireAngel ST-625 has been designed to make silencing and testing your smoke alarm easier.
|Alternative Product Codes||ST-625, ST-625R, st265|
2 x AA batteries
+4°C to +38°C
Up to 90%
The sticky pad is suitable for all battery operated smoke alarms. However, we cannot judge if battery alarms are suitable for your let property, as let properties usually require mains powered alarms. There is some advice to this in the governments guides to fire risk assessments. http://www.safelincs.co.uk/Fire-Risk-Assessment/ Also see the LACoRS guide for let properties.
BS 5839-6 recommends that one or two storey HMOs with an individual floor area of no more than 200sqm (not the total of both floors) should have a Grade D smoke alarm system installed. Grade D refers to mains powered smoke alarms with a back up battery power supply. The alarms can be interlinked either by wire or by radio signal and the system does not require a separate fire alarm panel. For HMOs of 3 storey or higher, a Grade A panel system would need to be installed. This can cover the whole of the building, or can be used just for the communal areas with a separate Grade D system installed for the individual dwellings. For both applications, the level of cover should be a minimum of LD3 (in all escape routes) but this may change according to the fire risk assessment.
The FireAngel 625 smoke alarm uses a different base plate. Therefore it would be necessary to install a fresh base plate if switching from one model to the other.
Every FireAngel FAST625 is supplied with the following components.
97 customers have given this product an overall rating of 4.7 out of 5
Rating: 4 / 5 Stars
Reviewed by: D L
The alarm is working as well as expected but i only installed it 2 months ago.
Published on: 8th March 2022
Rating: 5 / 5 Stars
Reviewed by: E M
Published on: 18th January 2021
Rating: 4 / 5 Stars
Reviewed by: P W
Good solid product. Found that when the base was fitted to the ceiling the outer unit was abit on the tight side to locate and fit but once fitted it was secure enough.
Published on: 16th June 2020